Application: Barrier-free emergency shower for horizontal mounting. Unit should be installed so that shower head is at least 82" above floor and 32" from wall or nearest obstruction.
ADA Compliance: When installed at recommended mounting heights, unit complies with ADA requirements for accessibility by handicapped persons (maximum height and reach and distance from obstructions).
Shower Head: 10" diameter orange ABS plastic.
Valve: 1" IPS chrome plated brass stay-open ball valve. Valve is US-made with chrome plated brass ball and Teflon® seals. Furnished with stainless steel actuating arm and 59 1/2" stainless steel pull rod.
Pipe & Fittings: 1" IPS galvanized steel nipple with orange ABS plastic elbow.
Supply: 1" NPT female inlet.
Sign: ANSI-compliant identification sign.